// CODE SNIPPET
230.51 Mounting Supports
JUMP TO FULL CODE CHAPTER
Cables that are not approved for mounting in contact with a building or other structure shall be mounted on insulating supports installed at intervals not exceeding 4.5 m (15 ft) and in a manner that maintains a clearance of not less than 50 mm (2 in.) from the surface over which they pass.
Individual open conductors shall be installed in accordance with Table 230.51(C). Where exposed to the weather, the conductors shall be mounted on insulators or on insulating supports attached to racks, brackets, or other approved means. Where not exposed to the weather, the conductors shall be mounted on glass or porcelain knobs.
Table 230.51(C) Supports
|Maximum Volts||Maximum Distance Between Supports||Minimum Clearance|
|Between Conductors||From Surface|
|*Where not exposed to weather.|
Related Code Sections
230.51 Wiring and Protection, Mounting Supports
in contact with a building or other structure shall be mounted on insulating supports installed at intervals not exceeding 4.5 m (15 ft) and in a manner ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 230 Services > 230.51 Mounting Supports
(D) Wiring Methods and Materials, Mounting of Conductor Supports
Where nails are used to mount knobs, they shall not be smaller than tenpenny. Where screws are used to mount knobs, or where nails or screws are used ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 398 Open Wiring on Insulators > 398.30 Securing and Supporting > (D) Mounting of Conductor Supports
184.108.40.206 Hydraulic Elevators,
The traveling sheave, if provided, shall be guided by means of suitable guide shoes and guide rails adequately mounted and supported ...
Safety Code for Elevators and Escalators 2016 of Minnesota > 3 Hydraulic Elevators > 3.23 Guide Rails, Guide-Rail Supports, and Fastenings > 3.23.2 Roped-Hydraulic Elevators > 220.127.116.11
(E) Wiring Methods and Materials, Separable Attachment Fittings
Outlet boxes required in 314.27 shall be permitted to support listed locking support and mounting receptacles used in combination with compatible ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 314 Outlet, Device, Pull, and Junction Boxes; Conduit Bodies; Fittings; And Handhole Enclosures > 314.27 Outlet Boxes > (E) Separable Attachment Fittings