// CODE SNIPPET
(B) Mounting and Location
Related Code Sections
(B) Special Occupancies, Mounting and Location
Service equipment shall be securely fastened to a solid backing and be installed so as to be protected from the weather, unless of weatherproof ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 525 Carnivals, Circuses, Fairs, and Similar Events > 525.10 Services > (B) Mounting and Location
(1) Equipment for General Use, Mounting Location
Heating panel sets shall be permitted to be secured to the lower face of joists or mounted in between joists, headers, or nailing strips ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 424 Fixed Electric Space-Heating Equipment > 424.93 Installation > (B) Heating Panel Sets > (1) Mounting Location
(1) Equipment for General Use, Location
be permitted to be open-mounted in locations accessible to qualified persons only. (b) Circuit breakers used to control oil-filled transformers in a vault ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 490 Equipment Over 1000 Volts, Nominal > 490.21 Circuit-Interrupting Devices > (A) Circuit Breakers > (1) Location
(C) Special Occupancies, Fixed Lighting Branch Circuits
are wall-mounted and located above hazardous (classified) locations. Exception: Sections 517.63(C)(1) and (C)(4) shall not apply in unclassified ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.63 Grounded Power Systems in Anesthetizing Locations > (C) Fixed Lighting Branch Circuits
(5) Special Equipment, Location, Wall-Mounted Luminaires
Luminaires mounted in walls shall be installed with the top of the luminaire lens not less than 450 mm (18 in.) below the normal water level ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 680 Swimming Pools, Fountains, and Similar Installations > 680.23 Underwater Luminaires > (A) General > (5) Location, Wall-Mounted Luminaires