// CODE SNIPPET
2204.2.3 Monitoring of Dispensing
JUMP TO FULL CODE CHAPTER
A control booth shall be located on the premises of every self-service automotive liquid motor fuel-dispensing facility. The control booth shall be an interior or exterior enclosure to which the public has no access. The certified attendant shall be present within the control booth while dispensing operations are conducted. The control booth shall be designed and located so that the certified attendant stationed therein shall have a full, unobstructed clear view of dispensing operations, except that mirrors and/or an approved closed-circuit television installation may be provided to afford the certified attendant a clear view of dispensing operations when the view from the control booth is partially or temporarily obstructed. For purposes of this section, the "clear" view provided by a closed-circuit television installation shall mean that the image on the monitor shall be of such brightness and resolution as to allow ready identification of individuals and easy observation of activities at all times of day. Two properly labeled manual switches, one that activates the fire extinguishing system, and one that electrically disconnects the liquid motor fuel-dispensing pumps, shall be located adjacent to each other within the control booth. A console that controls the self-service liquid motor fuel dispensers shall be provided within the control booth and within 5 feet (1524 mm) of the manual switches.