// CODE SNIPPET
10.6.10.6 Monitoring Integrity of Battery Charger
JUMP TO FULL CODE CHAPTER
Related Code Sections
10.6.10.6 Fundamentals, Monitoring Integrity of Battery Charger
Means for monitoring integrity appropriate for the batteries and charger employed shall be provided to detect a battery charger failure ...
National Fire Alarm and Signaling Code 2013 of Colorado > 10 Fundamentals > 10.6 Power Supplies > 10.6.10* Storage Batteries > 10.6.10.6 Monitoring Integrity of Battery Charger
18.104.22.168 Emergency Communications Systems (ECS), System Monitoring
booster(s) and power supply(ies) that are annunciated by the fire alarm system and comply with the following: The integrity of the circuit monitoring ...
National Fire Alarm and Signaling Code 2013 of Colorado > 24 Emergency Communications Systems (ECS) > 24.5 Two-Way, In-Building Emergency Communications Systems > 24.5.2* Two-Way Radio Communications Enhancement Systems > 22.214.171.124 System Monitoring
126.96.36.199 Public Emergency Alarm Reporting Systems,
Solar photovoltaic power systems shall be monitored for integrity ...
National Fire Alarm and Signaling Code 2013 of Colorado > 27 Public Emergency Alarm Reporting Systems > 27.6 Alarm Boxes > 27.6.6 Wireless Network Boxes > 188.8.131.52
1184.108.40.206 Energy Systems, Battery Chargers
Battery chargers shall be compatible with the battery chemistry and the manufacturer's electrical ratings and charging specifications. Battery ...
Fire Code 2018 of Colorado > 12 Energy Systems > 1206 Electrical Energy Storage Systems > 1206.2 Stationary Storage Battery Systems > 1206.2.10 Storage Batteries and Equipment > 1220.127.116.11 Battery Chargers
309.3 General Requirements, Battery Chargers
Battery chargers shall be of an approved type. Combustible storage shall be kept not less than 3 feet (915 mm) from battery chargers. Battery ...
Fire Code 2018 of Colorado > 3 General Requirements > 309 Powered Industrial Trucks and Equipment > 309.3 Battery Chargers