// CODE SNIPPET
(C) Minimum Thickness of Enclosure Metal
JUMP TO FULL CODE CHAPTER
Sheet copper or aluminum shall be at least 0.51 mm (0.020 in.) thick. Sheet steel shall be at least 0.41 mm (0.016 in.) thick.
Related Code Sections
(C) Special Equipment, Minimum Thickness of Enclosure Metal
Sheet copper or aluminum shall be at least 0.51 mm (0.020 in.) thick. Sheet steel shall be at least 0.41 mm (0.016 in.) thick ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 600 Electric Signs and Outline Lighting > 600.8 Enclosures > (C) Minimum Thickness of Enclosure Metal
(B) Wiring Methods and Materials, Thickness of Metal
( 3 / 32 in.) thick. Other cast metal boxes or conduit bodies shall have a wall thickness not less than 3.17 mm ( 1 / 8 in.). Exception No. 1 ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 314 Outlet, Device, Pull, and Junction Boxes; Conduit Bodies; Fittings; And Handhole Enclosures > 314.40 Metal Boxes, Conduit Bodies, and Fittings > (B) Thickness of Metal
(B) Special Equipment, Metal Enclosures Grounded
All metal enclosures of power-supply apparatus for the direct-current cell line process operating with a power supply over 50 volts shall be grounded ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 668 Electrolytic Cells > 668.11 Direct-Current Cell Line Process Power Supply > (B) Metal Enclosures Grounded
2.3.4 Electric Elevators, Counterweight Runway Enclosures
The partition shall be noncombustible. Unperforated metal partitions shall be equal to or stronger than 1.2 mm (0.047 in.) thick sheet steel ...
Safety Code for Elevators and Escalators 2016 of Minnesota > 2 Electric Elevators > 2.3 Location and Guarding of Counterweights > 2.3.4 Counterweight Runway Enclosures