Station outlets and inlets for medical gas and vacuum systems shall be provided as listed in Table 1305.3.
|LOCATION||OXYGEN||MEDICAL VACUUM||MEDICAL AIR||NITROUS OXIDE||NITROGEN||HELIUM||CARBON DIOXIDE|
|Patient rooms for medical/surgical, obstetrics, and pediatrics||1/bed||1/bed||1/bed||-||-||-||-|
|Examination/treatment for nursing units||1/bed||1/bed||-||-||-||-||-|
|Intensive care ( all)||3/bed||3/bed||2/bed||-||-||-||-|
|General operating rooms||2/room||3/room4||2/room||1/room||1/room||-||-|
|Cystoscopic and special invasive procedures||2/room||3/room4||2/room||-||-||-||-|
|Recovery delivery and labor/delivery/recovery rooms2||2/bed
|First aid and emergency treatment3||1/bed||1/bed4||1/bed||-||-||-||-|
- 1 Includes pediatric nursery.
- 2 Includes obstetric recovery.
- 3 Emergency trauma rooms used for surgical procedures shall be classified as general operating rooms.
- 4 Vacuum inlets required are in addition to inlets used as part of a scavenging system for removal of anesthetizing gases.