// CODE SNIPPET
620.12 Minimum Size of Conductors
JUMP TO FULL CODE CHAPTER
For lighting circuits, 14 AWG copper, 20 AWG copper or larger conductors shall be permitted in parallel, provided the ampacity is equivalent to at least that of 14 AWG copper.
For other circuits, 20 AWG copper.
24 AWG copper. Smaller size listed conductors shall be permitted.