// CODE SNIPPET
809.1 Minimum Fixtures
JUMP TO FULL CODE CHAPTER
Where the occupant load of the story is increased by more than 20 percent, plumbing fixtures for the story shall be provided in quantities specified in the International Plumbing Code based on the increased occupant load.
Related Code Sections
809.1 Alterations—Level 2, Minimum Fixtures
Where the occupant load of the story is increased by more than 20 percent, plumbing fixtures for the story shall be provided in quantities specified ...
Existing Building Code 2018 of Illinois > 8 Alterations—Level 2 > 809 Plumbing > 809.1 Minimum Fixtures
2902.1 Plumbing Systems, Minimum Number of Fixtures
Plumbing fixtures shall be provided in the minimum number as shown in Table 2902.1 based on the actual use of the building or space. Uses not shown ...
Building Code 2018 of Illinois > 29 Plumbing Systems > 2902 Minimum Plumbing Facilities > 2902.1 Minimum Number of Fixtures
1018.1 Means of Egress, General
, displays and similar fixtures or equipment. The minimum width or required capacity of aisles shall be unobstructed. Exception: Encroachments ...
410.52 Equipment for General Use, Conductor Insulation
the conductors will be subjected. Informational Note: For ampacity of fixture wire, maximum operating temperature, voltage limitations, minimum wire ...
National Electrical Code 2017 of Illinois > 4 Equipment for General Use > 410 Luminaires, Lampholders, and Lamps > 410.52 Conductor Insulation
604.5.2 Plumbing Elements and Facilities, Rear Wall
minimum, centered on the water closet, where wall space does not permit a length of 36 inches (915 mm) minimum due to the location of a recessed fixture ...
2018 Illinois Accessibility Code > 6 Plumbing Elements and Facilities > 604 Water Closets and Toilet Compartments > 604.5 Grab Bars > 604.5.2 Rear Wall