// CODE SNIPPET
M2003.2 Minimum Capacity
JUMP TO FULL CODE CHAPTER
The minimum capacity of expansion tanks shall be determined from Table M2003.2.
For SI: 1 gallon= 3.785 L, 1 pound per square inch gauge = 6.895 kPa,
°C = [(°F)-32]/1.8.
Related Code Sections
M2003.2 Boilers and Water Heaters, Minimum Capacity
The minimum capacity of expansion tanks shall be determined from Table M2003.2. TABLE M2003.2 EXPANSION TANK MINIMUM CAPACITY ...
2015 Michigan Residential Code > 20 Boilers and Water Heaters > M2003 Expansion Tanks > M2003.2 Minimum Capacity
P3007.6 Sanitary Drainage, Capacity
be capable of handling spherical solids with a diameter of up to and including 1 inch (25.4 mm). The minimum capacity of a pump or ejector based ...
G2428.2.1 Fuel Gas, (504.2.1) Vent Obstructions
with the following: The maximum capacity of the vent system shall be determined using the "NAT Max" column. The minimum capacity shall be determined ...
2015 Michigan Residential Code > 24 Fuel Gas > G2428 (504) Sizing of Category I Appliance Venting Systems > G2428.2 (504.2) Application of Single Appliance Vent Tables G2428.2(1) and G2428.2(2) > G2428.2.1 (504.2.1) Vent Obstructions
1005.5 Means of Egress, Distribution of Minimum Width and Required Capacity
exit , or access to one exit , shall not reduce the available capacity or width to less than 50 percent of the required capacity or width ...
2015 Michigan Building Code > 10 Means of Egress > 1005 Means of Egress Sizing > 1005.5 Distribution of Minimum Width and Required Capacity
1028.2 Means of Egress, Exit Discharge Width or Capacity
The minimum width or required capacity of the exit discharge shall be not less than the minimum width or required capacity of the exits being ...
2015 Michigan Building Code > 10 Means of Egress > 1028 Exit Discharge > 1028.2 Exit Discharge Width or Capacity