// CODE SNIPPET
314.4 Metal Boxes
Related Code Sections
(C) Wiring and Protection, Metal Boxes
A connection used for no other purpose shall be made between the metal box and the equipment grounding conductor(s) in accordance with 250.8 ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 250 Grounding and Bonding > 250.148 Continuity of Equipment Grounding Conductors and Attachment in Boxes > (C) Metal Boxes
314.4 Wiring Methods and Materials, Metal Boxes
Metal boxes shall be grounded and bonded in accordance with Parts I, IV, V, VI, VII, and X of Article 250 as applicable, except as permitted ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 314 Outlet, Device, Pull, and Junction Boxes; Conduit Bodies; Fittings; And Handhole Enclosures > 314.4 Metal Boxes
(A) Special Occupancies, Equipment to Be Connected to Equipment Grounding Conductor
: Metal boxes, metal cabinets, and all other metal enclosures Metal frames of utilization equipment Grounding terminals of grounding-type ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 555 Marinas, Boatyards, Floating Buildings, and Commercial and Noncommercial Docking Facilities > 555.37 Equipment Grounding Conductor > (A) Equipment to Be Connected to Equipment Grounding Conductor