// CODE SNIPPET
JUMP TO FULL CODE CHAPTER
Only glass (Pyrex) and stainless steel shall be used for dialysis, reverse osmosis or deionized water piping.
Exception: PVC, CPVC and Polypropylene piping be permitted in reverse osmosis and deionized water systems.
Related Code Sections
P-305.4 Materials, Medical
Only glass (Pyrex) and stainless steel shall be used for dialysis, reverse osmosis or deionized water piping. Exception: PVC, CPVC ...
Philadelphia Plumbing Code > 3 Materials > P-305 Materials for Plumbing Installations > P-305.4 Medical
1103.10 Construction Requirements for Existing Buildings, Medical Gases
Medical gases stored and transferred in health-care-related facilities shall be in accordance with Chapter 53 ...
2018 Philadelphia Fire Code > 11 Construction Requirements for Existing Buildings > 1103 Fire Safety Requirements for Existing Buildings > 1103.10 Medical Gases
1106.7.2 Accessibility, Medical Facilities
A passenger loading zone shall be provided at an accessible entrance to licensed medical and long-term care facilities where people receive ...
2018 Philadelphia Building Code > 11 Accessibility > 1106 Parking and Passenger Loading Facilities > 1106.7 Passenger Loading Zones > 1106.7.2 Medical Facilities
Section 1202 Special Piping and Storage Systems, Medical Gases
Nonflammable medical gas systems, inhalation anesthetic systems and vacuum piping systems shall be designed and installed in accordance with NFPA 99 ...
3503.1.1.1 Flammable Gases and Flammable Cryogenic Fluids, Medical Gases
Medical gas system supply cylinders shall be located in medical gas storage rooms or gas cabinets as set forth in Section 3006 ...
Philadelphia Fire Code > 35 Flammable Gases and Flammable Cryogenic Fluids > 3503 General Requirements > 3503.1 Quantities Not Exceeding the Maximum Allowable Quantity Per Control Area > 3503.1.1 Special Limitations for Indoor Storage and Use > 3503.1.1.1 Medical Gases