469.4.11 Mechanical System Standards
For piped systems, the number of station outlets shall meet the needs of the functional program. However, the minimum number of station outlets shall be as described in Table 4126.96.36.199.3.
MINIMUM STATION OUTLETS FOR PIPED GAS SYSTEMS IN OFFICE SURGERY SUITES
|Class B and C||2||2*|
|Post Operative Recovery||1||1|
* An additional outlet shall be provided for anesthesia evacuation if necessary.