// CODE SNIPPET
5003.8.6.3 Maximum Number of Cylinders Per Gas Cabinet
Related Code Sections
5003.8.6.3 Hazardous Materials—General Provisions, Maximum Number of Cylinders Per Gas Cabinet
The number of cylinders contained in a single gas cabinet shall not exceed three ...
Fire Code 2018 of Kansas > 50 Hazardous Materials—General Provisions > 5003 General Requirements > 5003.8 Construction Requirements > 5003.8.6 Gas Cabinets > 5003.8.6.3 Maximum Number of Cylinders Per Gas Cabinet
6004.1.2 Highly Toxic and Toxic Materials, Gas Cabinets
not be used as the sole means of exhaust for any room or area. The maximum number of cylinders located in a single gas cabinet shall not exceed three, except ...
Fire Code 2018 of Kansas > 60 Highly Toxic and Toxic Materials > 6004 Highly Toxic and Toxic Compressed Gases > 6004.1 General > 6004.1.2 Gas Cabinets
5303.7.10 Compressed Gases, Gas Cabinets
Where gas cabinets are provided as a means to separate compressed gas containers, cylinders and tanks from exposure hazards, such gas cabinets ...
Fire Code 2018 of Kansas > 53 Compressed Gases > 5303 General Requirements > 5303.7 Separation From Hazardous Conditions > 5303.7.10 Gas Cabinets
5803.1.1.1 Flammable Gases and Flammable Cryogenic Fluids, Medical Gases
Medical gas system supply cylinders shall be located in medical gas storage rooms or gas cabinets as set forth in Section 5306 ...
Fire Code 2018 of Kansas > 58 Flammable Gases and Flammable Cryogenic Fluids > 5803 General Requirements > 5803.1 Quantities Not Exceeding the Maximum Allowable Quantity Per Control Area > 5803.1.1 Special Limitations for Indoor Storage and Use > 5803.1.1.1 Medical Gases
502.9.7.1 Exhaust Systems, Gas Cabinets
: The average ventilation velocity at the face of gas cabinet access ports or windows shall be not less than 200 feet per minute (1.02 m/s) with a minimum ...
Mechanical Code 2018 of Kansas > 5 Exhaust Systems > 502 Required Systems > 502.9 Hazardous Materials—Requirements for Specific Materials > 502.9.7 Highly Toxic and Toxic Compressed Gases—Any Quantity > 502.9.7.1 Gas Cabinets