// CODE SNIPPET
[NY] 1206.12.6 Maximum Enclosure Size
JUMP TO FULL CODE CHAPTER
Outdoor walkin energy storage system units housing energy storage systems shall not exceed 4,028 cubic feet (114 m3), not including bolt-on HVAC and related equipment, as approved. Outdoor walk-in energy storage system units exceeding these limitations shall be considered indoor installations and comply with the requirements in Section 1206.14.
Related Code Sections
1206.12.6 Energy Systems, Maximum Enclosure Size
Outdoor walkin energy storage system units housing energy storage systems shall not exceed 4,028 cubic feet (114 m3), not including bolt-on HVAC ...
2020 Fire Code of NYS > 12 Energy Systems > 1206 Electrical Energy Storage Systems > 1206.12 Electrochemical Energy Storage System Protection > 1206.12.6 Maximum Enclosure Size
3704.2.2.7.3 Highly Toxic and Toxic Materials, Sizing
Treatment systems shall be sized to process the maximum worst-case release of gas based on the maximum flow rate of release from the largest vessel ...
2010 Fire Code of NY > 37 Highly Toxic and Toxic Materials > 3704 Highly Toxic and Toxic Compressed Gases > 3704.2 Indoor Storage and Use > 3704.2.2 General Indoor Requirements > 3704.2.2.7 Treatment Systems > 3704.2.2.7.3 Sizing