// CODE SNIPPET
[F] 902.1.2 Marking on Access Doors
JUMP TO FULL CODE CHAPTER
Related Code Sections
902.1.2 Fire Protection and Life Safety Systems, Marking on Access Doors
Access doors for automatic sprinkler system riser rooms and fire pump rooms shall be labeled with an approved sign. The lettering shall ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 902 Fire Pump and Riser Room Size > 902.1 Pump and Riser Room Size > 902.1.2 Marking on Access Doors
1013.1 Means of Egress, Where Required
Exits and exit access doors shall be marked by an approved exit sign readily visible from any direction of egress travel. The path of egress ...
905.7 Fire Protection and Life Safety Systems, Cabinets
with the background color, indicating the equipment contained therein. Exception: Doors not large enough to accommodate a written sign shall be marked ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 905 Standpipe Systems > 905.7 Cabinets
914.1 Fire Protection and Life Safety Systems, Shaftway Markings
Outside openings accessible to the fire department and that open directly on a hoistway or shaftway communicating ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 914 Emergency Responder Safety Features > 914.1 Shaftway Markings
490.53 Equipment for General Use, Enclosures
these units can be reset without opening locked doors. With doors closed, safe access for normal operation of these units shall be provided ...
National Electrical Code 2017 of Illinois > 4 Equipment for General Use > 490 Equipment Over 1000 Volts, Nominal > 490.53 Enclosures