Section 2310 Marine Motor Fuel-Dispensing Facilities
Class I, II or IIIA liquids stored inside of buildings used for marine motor fuel-dispensing facilities shall be stored in approved containers or portable tanks. Storage of Class I liquids shall not exceed 10 gallons (38 L).
Fueling of floating marine craft with Class II or III fuels at other than a marine motor fuel-dispensing facility shall be in accordance with all of the following:
- The premises and operations shall be approved by the fire code official.
- Tank vehicles and fueling operations shall comply with Section 5706.6.
- The dispensing nozzle shall be of the listed automatic-closing type without a latch-open device.
- Nighttime deliveries shall only be made in lighted areas.
- The tank vehicle flasher lights shall be in operation while dispensing.
- Fuel expansion space shall be left in each fuel tank to prevent overflow in the event of temperature increase.
Containers with tight-fitting or self-closing lids shall be provided for temporary storage of combustible debris, rubbish and waste material. The rubbish containers shall be constructed entirely of materials that comply with any one of the following:
- Noncombustible materials.
- Materials that meet a peak rate of heat release not exceeding 300 kW/m2 when tested in accordance with ASTM E1354 at an incident heat flux of 50 kW/m2 in the horizontal orientation.
Warning signs shall be prominently displayed at the face of each wharf, pier or float at such elevation as to be clearly visible from the decks of marine craft being fueled. Such signs shall have letters not less than 3 inches (76 mm) in height on a background of contrasting color bearing the following or approved equivalent wording:
NO SMOKING—STOP ENGINE WHILE FUELING,
SHUT OFF ELECTRICITY
DO NOT START ENGINE UNTIL AFTER BELOW
DECK SPACES ARE VENTILATED.
Portable fire extinguishers in accordance with Section 906, each having a minimum rating of 20-B:C, shall be provided as follows: