// CODE SNIPPET
18.104.22.168 Maintenance of Piping Systems
JUMP TO FULL CODE CHAPTER
This maintenance shall include inspection for physical damage, leak tightness, ground system integrity, vent system operation, equipment identification, warning signs, operator information and training records, scheduled maintenance and retest records, alarm operation, and other safety-related features. [55:22.214.171.124]
Scheduled maintenance and retest activities shall be formally documented, and records shall be maintained a minimum of 3 years. [55:126.96.36.199]
Related Code Sections
188.8.131.52 Compressed Gases and Cryogenic Fluids, Maintenance of Piping Systems
Maintenance of flammable gas system piping and components shall be performed annually by a qualified representative of the equipment owner. [ 55 ...
Fire Code 2018 of West Virginia > 63 Compressed Gases and Cryogenic Fluids > 63.3 Compressed Gases > 63.3.6 Flammable Gases > 184.108.40.206 Maintenance of Piping Systems
G2412.1 Fuel Gas, (401.1) Scope
This section shall govern the design, installation, modification and maintenance of piping systems . The applicability of this code to piping ...
401.1 Gas Piping Installations, Scope
This chapter shall govern the design, installation, modification and maintenance of piping systems. The applicability of this code to piping ...
220.127.116.11 Flammable and Combustible Liquids,
This section shall apply to the design, installation, testing, operation, and maintenance of piping systems for flammable and combustible liquids ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.27 Piping Systems > 66.27.1 Scope > 18.104.22.168
22.214.171.124.2.4 Fire Protection Systems,
Compressors used in conjunction with dry pipe sprinkler systems shall be maintained in accordance with the manufacturer's instructions. [ 25: 126.96.36.199] ...
Fire Code 2018 of West Virginia > 13 Fire Protection Systems > 13.3 Automatic Sprinklers > 13.3.3 Inspection, Testing, and Maintenance > 188.8.131.52 Sprinkler Systems > 184.108.40.206.2* Dry Pipe Systems > 220.127.116.11.2.4