// CODE SNIPPET
1609.6.1 Main Windforce-Resisting System
JUMP TO FULL CODE CHAPTER
Related Code Sections
1609.6.1 Structural Design, Main Windforce-Resisting System
The load due to wind pressure, W , on the main windforce-resisting system shall be based on exposure category and risk category as indicated ...
2019 Chicago Building Code > 16 Structural Design > 1609 Wind Loads > 1609.6 Alternative Wind Loads for Enclosed Structure With Mean Roof Height of 60 Feet or Less > 1609.6.1 Main Windforce-Resisting System
3.5.5 Definitions, Cross Mains
The pipes supplying the branch lines, either directly or through riser nipples ...
Standard for the Installation of Sprinkler Systems 2016 of Chicago > 3 Definitions > 3.5* System Component Definitions > 3.5.5 Cross Mains
(A) Wiring and Protection, Material
Main bonding jumpers and system bonding jumpers shall be of copper or other corrosion-resistant material. A main bonding jumper and a system bonding ...
National Electrical Code 2017 of Chicago > 2 Wiring and Protection > 250 Grounding and Bonding > 250.28 Main Bonding Jumper and System Bonding Jumper > (A) Material
184.108.40.206 Special Occupancy Requirements, Yard Mains
The underground yard fire main loop shall be installed to furnish anticipated water requirements, and the following criteria also shall be met ...
Standard for the Installation of Sprinkler Systems 2016 of Chicago > 22 Special Occupancy Requirements > 22.27 Advanced Light Water Reactor Electric Generating Plants > 22.27.1 Design Requirements > 220.127.116.11 Yard Mains
18.104.22.168 Systems Acceptance, Main Drain Valves
The main drain valve shall be opened and remain open until the system pressure stabilizes ...
Standard for the Installation of Sprinkler Systems 2016 of Chicago > 25 Systems Acceptance > 25.2 Acceptance Requirements > 25.2.3 System Operational Tests > 22.214.171.124 Main Drain Valves