// CODE SNIPPET
(C) Luminaires Connected Together
JUMP TO FULL CODE CHAPTER
Luminaires designed for end-to-end connection to form a continuous assembly, or luminaires connected together by recognized wiring methods, shall be permitted to contain the conductors of a 2-wire branch circuit, or one multiwire branch circuit, supplying the connected luminaires and shall not be required to be listed as a raceway. One additional 2-wire branch circuit separately supplying one or more of the connected luminaires shall also be permitted.
Related Code Sections
(C) Equipment for General Use, Luminaires Connected Together
Luminaires designed for end-to-end connection to form a continuous assembly, or luminaires connected together by recognized wiring methods, shall ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 410 Luminaires, Lampholders, and Lamps > 410.64 Luminaires as Raceways > (C) Luminaires Connected Together
(E) Special Occupancies, Grounding Continuity
Where more than one equipment grounding or bonding conductor of a branch circuit enters a box, all such conductors shall be connected together using ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 551 Recreational Vehicles and Recreational Vehicle Parks > 551.55 Interior Equipment Grounding > (E) Grounding Continuity