// CODE SNIPPET
E4003.13 Luminaire Wiring-General
JUMP TO FULL CODE CHAPTER
Wiring on or within luminaires shall be neatly arranged and shall not be exposed to physical damage. Excess wiring shall be avoided. Conductors shall be arranged so that they are not subjected to temperatures above those for which the conductors are rated. (410.48)
Luminaires shall be wired so that the screw shells of lampholders will be connected to the same luminaire or circuit conductor or terminal. The grounded conductor shall be connected to the screw shell.
Luminaires shall not be used as raceways for circuit conductors except where such luminaires are listed and marked for use as a raceway or are identified for through-wiring. Luminaires designed for end-to-end connection to form a continuous assembly, and luminaires connected together by recognized wiring methods, shall not be required to be listed as a raceway where they contain the conductors of one 2-wire branch circuit or one multiwire branch circuit and such conductors supply the connected luminaires. One additional 2-wire branch circuit that separately supplies one or more of the connected luminaires shall also be permitted. [410.64(A), (B), and (C)]
Related Code Sections
E4003.13 Devices and Luminaries, Luminaire Wiring-General
Wiring on or within luminaires shall be neatly arranged and shall not be exposed to physical damage. Excess wiring shall be avoided. Conductors shall ...
2015 Michigan Residential Code > 40 Devices and Luminaries > E4003 Luminaires > E4003.13 Luminaire Wiring-General
E3905.1.6 Power and Lighting Distribution, Luminaires
Where a luminaire is listed to be used as a raceway, a box or conduit body shall not be required for wiring installed therein. [300.15(1)] ...
2015 Michigan Residential Code > 39 Power and Lighting Distribution > E3905 Boxes, Conduit Bodies and Fittings > E3905.1 Box, Conduit Body or Fitting-Where Required > E3905.1.6 Luminaires
E4202.1 Swimming Pools, General
Wiring methods used in conjunction with permanently installed swimming pools, spas, hot tubs or hydromassage bathtubs shall be installed ...
2015 Michigan Residential Code > 42 Swimming Pools > E4202 Wiring Methods for Pools, Spas, Hot Tubs and Hydromassage Bathtubs > E4202.1 General
Section E4004 Devices and Luminaries, Luminaire Installation
the disconnection of any part of the wiring. Luminaires that are connected by attachment plugs and receptacles meet the requirement of this section ...