// CODE SNIPPET
606.2 Location of Shutoff Valves
JUMP TO FULL CODE CHAPTER
Shutoff valves shall be installed in the following locations:
- On the fixture supply to each plumbing fixture other than bathtubs and showers in one- and two-family residential occupancies, and other than in individual sleeping units that are provided with unit shutoff valves in hotels, motels, boarding houses and similar occupancies.
- On the water supply pipe to each sillcock.
- On the water supply pipe to each appliance or mechanical equipment.
Related Code Sections
606.2 Water Supply and Distribution, Location of Shutoff Valves
Shutoff valves shall be installed in the following locations: On the fixture supply to each plumbing fixture other than bathtubs and showers in one ...
Plumbing Code 2018 of Kansas > 6 Water Supply and Distribution > 606 Installation of the Building Water Distribution System > 606.2 Location of Shutoff Valves
403.7.1.1 Emergency Planning and Preparedness, Plans and Diagrams
the approximate plan for each area, the amount and type of HPM stored, handled and used, locations of shutoff valves for HPM supply piping, emergency telephone ...
Fire Code 2018 of Kansas > 4 Emergency Planning and Preparedness > 403 Emergency Preparedness Requirements > 403.7 Group H Occupancies > 403.7.1 Group H-5 Occupancies > 403.7.1.1 Plans and Diagrams
P2911.8.1 Water Supply and Distribution, Bypass Valve
and storage tank or drainfield connection. Bypass valves shall be installed in accessible locations. Two shutoff valves shall not be installed ...
Residential Code 2018 of Kansas > 29 Water Supply and Distribution > P2911 On-Site Nonpotable Water Reuse Systems > P2911.8 Valves > P2911.8.1 Bypass Valve
1205.10 Energy Systems, Manual Shutoff
shutoff valve shall be permitted. If the stationary fuel cell power system is located indoors, the shutoff valve shall be located outside ...
Fire Code 2018 of Kansas > 12 Energy Systems > 1205 Stationary Fuel Cell Power Systems > 1205.10 Manual Shutoff