// CODE SNIPPET
18.104.22.168* Location of Piping
JUMP TO FULL CODE CHAPTER
Only piping for product, utility, or fire protection purposes directly connected to a tank or tanks within a single diked area shall be routed through a diked area, a remote impoundment area, a spillway draining to a remote impoundment area, or above a storage tank drainage area where the piping can be exposed to a fire.
Exception: Piping for other product lines and from adjacent tanks is permitted to be routed through such areas if engineering designs are provided to incorporate features to prevent the piping from creating an exposure hazard. [30:22.12.1]
Related Code Sections
22.214.171.124* Flammable and Combustible Liquids, Location of Piping
Only piping for product, utility, or fire protection purposes directly connected to a tank or tanks within a single diked area shall be routed ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.22 Storage of Liquids in Tanks — Aboveground Storage Tanks > 66.22.12 Equipment, Piping, and Fire Protection Systems in Remote Impoundment Areas and Diked Areas > 126.96.36.199* Location of Piping
(A) Special Occupancies, Class II, Division 1
In Class II, Division 1 locations, ventilating pipes, including their connections to motors or to the dust-ignitionproof enclosures for other ...
National Electrical Code 2017 of West Virginia > 5 Special Occupancies > 502 Class II Locations > 502.128 Ventilating Piping > (A) Class II, Division 1
1107.2 Refrigeration, Piping Location
the floor unless the piping is located against the ceiling of such space. Refrigerant piping shall not be placed in any elevator, dumbwaiter or other shaft ...
Mechanical Code 2015 of West Virginia > 11 Refrigeration > 1107 Refrigerant Piping > 1107.2 Piping Location
405.3.3 Fixtures, Faucets and Fixture Fittings, Location of Fixtures and Piping
Piping, fixtures or equipment shall not be located in such a manner as to interfere with the normal operation of windows, doors or other means ...
Plumbing Code 2015 of West Virginia > 4 Fixtures, Faucets and Fixture Fittings > 405 Installation of Fixtures > 405.3 Setting > 405.3.3 Location of Fixtures and Piping
M1411.7 Heating and Cooling Equipment and Appliances, Location and Protection of Refrigerant Piping
Refrigerant piping installed within 1 1 / 2 inches (38 mm) of the underside of roof decks shall be protected from damage caused by nails and other ...
Residential Code 2015 of West Virginia > 14 Heating and Cooling Equipment and Appliances > M1411 Heating and Cooling Equipment > M1411.7 Location and Protection of Refrigerant Piping