// CODE SNIPPET
Section 2303 Location of Dispensing Devices
JUMP TO FULL CODE CHAPTER
Dispensing devices shall be located as follows:
- Ten feet (3048 mm) or more from lot lines.
- Such that all portions of the vehicle being fueled will be on the premises of the motor fuel-dispensing facility.
- Such that the nozzle, where the hose is fully extended, will not reach within 5 feet (1524 mm) of building openings.
- Twenty feet (6096 mm) or more from fixed sources of ignition.
An approved emergency disconnect switch shall be provided at an approved location to stop the transfer of fuel to the fuel dispensers in the event of a fuel spill or other emergency. The emergency disconnect switch for exterior fuel dispensers shall be provided with ready access and shall be located within 100 feet (30 480 mm) of, but not less than 20 feet (6096 mm) from, the fuel dispensers. For interior fuel-dispensing operations, the emergency disconnect switch shall be provided with ready access and be installed at an approved location. Such devices shall be distinctly labeled as: EMERGENCY FUEL SHUTOFF. Signs shall be provided in approved locations.
The height of the emergency disconnect switch shall be not less than 42 inches (1067 mm) and not more than 48 inches (1372 mm) measured vertically, from the floor level to the activating button.