// CODE SNIPPET
[F] 905.5 Location of Class II Standpipe Hose Connections
JUMP TO FULL CODE CHAPTER
Class II standpipe hose connections located so that all portions of the building are within 30 feet (9144 mm) of a nozzle attached to 100 feet (30 480 mm) of hose. Class II standpipe hose connections shall be located where they will have ready access.
Fire-resistance-rated protection of risers and laterals of Class II standpipe systems is not required.
A minimum 1-inch (25 mm) hose shall be allowed to be used for hose stations in light-hazard occupancies where investigated and listed for this service and where approved by the fire code official.