Rooms containing capacitor energy storage systems shall be separated from the following occupancies by fire barriers or horizontal assemblies, or both, constructed in accordance with the California Building Code.
Capacitor energy storage systems shall be segregated into capacitor arrays not exceeding 50 kWh (180 megajoules) each. Each array shall be spaced not less than 3 feet (914 mm) from other arrays and from walls in the storage room or area. The storage arrangements shall comply with Chapter 10.
Approved signs shall be provided on doors or in locations adjacent to the entrances to capacitor energy storage system rooms and shall include the following or equivalent verbiage and information:.
- "CAPACITOR ENERGY STORAGE ROOM."
- "THIS ROOM CONTAINS ENERGIZED ELECTRICAL CIRCUITS."
- An identification of the type of capacitors present and the potential hazards associated with the capacitor type.
Capacitor energy systems located outdoors shall comply with Sections 1188.8.131.52 through 1184.108.40.206.4 in addition to all applicable requirements of Section 1206.3. Installations in outdoor enclosures or containers that can be occupied for servicing, testing, maintenance and other functions shall be treated as capacitor storage rooms.
Capacitor energy systems located outdoors shall be not less than 5 feet (1524 mm) from the following:
- Lot lines.
- Public ways.
- Stored combustible materials.
- Hazardous materials.
- High-piled stock.
- Other exposure hazards.
Exception: The fire code official is authorized to approve lesser separation distances if large-scale fire and fault condition testing conducted or witnessed and reported by an approved testing laboratory is provided showing that a fire involving the system will not adversely impact occupant egress from adjacent buildings, or adversely impact adjacent stored materials or structures.
Capacitor energy storage systems located outdoors shall be separated from any means of egress as required by the fire code official to ensure safe egress under fire conditions, but not less than 10 feet (3048 mm).
Exception: The fire code official is authorized to approve lesser separation distances if large-scale fire and fault condition testing conducted or witnessed and reported by an approved testing laboratory is provided showing that a fire involving the system will not adversely impact occupant egress.