// CODE SNIPPET
[F] 418.104.22.168 Liquid Storage Rooms
JUMP TO FULL CODE CHAPTER
Liquid storage rooms shall be constructed in accordance with the following requirements:
- Rooms greater than 500 square feet (46.5 m2) in area, shall have no fewer than one exterior door approved for fire department access.
- Rooms shall be separated from other areas by fire barriers constructed in accordance with Section 707 or horizontal assemblies constructed in accordance with Section 711, or both. The fire-resistance rating shall be not less than 1 hour for rooms up to 150 square feet (13.9 m2) in area and not less than 2 hours where the room is more than 150 square feet (13.9 m2) in area.
- Shelving, racks and wainscotting in such areas shall be of noncombustible construction or wood of not less than 1-inch (25 mm) nominal thickness or fire-retardant-treated wood complying with Section 2303.2.
- Rooms used for the storage of Class I flammable liquids shall not be located in a basement.
Related Code Sections
2703.3.3 Semiconductor Fabrication Facilities, Liquid Storage Rooms
Liquid storage rooms shall comply with Chapter 57 and the California Building Code ...
Los Angeles Fire Code > 27 Semiconductor Fabrication Facilities > 2703 General Safety Provisions > 2703.3 Construction Requirements > 2703.3.3 Liquid Storage Rooms
422.214.171.124 Special Detailed Requirements Based on Use and Occupancy, Liquid Storage Rooms
Liquid storage rooms shall be constructed in accordance with the following requirements: Rooms greater than 500 square feet (46.5 m 2 ) in area ...
Los Angeles Building Code > 4 Special Detailed Requirements Based on Use and Occupancy > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.11 Group H-5 > 415.11.5 HPM Rooms, Gas Rooms, Liquid Storage Room Construction > 4126.96.36.199 Liquid Storage Rooms
507.8.1.1.2 General Building Heights and Areas, Liquid Storage Rooms
Liquid storage rooms having a floor area of not more than 1,000 square feet (93 m 2 ) need not be located on the outer perimeter where ...
Los Angeles Building Code > 5 General Building Heights and Areas > 507 Unlimited Area Buildings > 507.8 Group H-2, H-3 and H-4 Occupancies > 507.8.1 Allowable Area > 507.8.1.1 Located Within the Building > 507.8.1.1.2 Liquid Storage Rooms
5704.3.7 Flammable and Combustible Liquids, Liquid Storage Rooms
Liquid storage rooms shall comply with Sections 5704.3.7.1 through 5704.3.7.5.2 ...
Los Angeles Fire Code > 57 Flammable and Combustible Liquids > 5704 Storage > 5704.3 Container and Portable Tank Storage > 5704.3.7 Liquid Storage Rooms
5104.5 Aerosols, Storage in Inside Flammable Liquid Storage Rooms
Inside flammable liquid storage rooms shall comply with Section 5704.3.7. The maximum quantities of aerosol products shall comply with Section ...
Los Angeles Fire Code > 51 Aerosols > 5104 Inside Storage of Aerosol Products > 5104.5 Storage in Inside Flammable Liquid Storage Rooms