// CODE SNIPPET
1107.8.1 Liquid Receivers
JUMP TO FULL CODE CHAPTER
Systems containing 100 pounds (45 kg) or more of a refrigerant, other than systems utilizing nonpositive displacement compressors, shall have stop valves, in addition to those required by Section 1107.8, on each inlet of each liquid receiver. Stop valves shall not be required on the inlet of a receiver in a condensing unit, nor on the inlet of a receiver that is an integral part of the condenser.
Related Code Sections
1107.8.1 Refrigeration, Liquid Receivers
valves, in addition to those required by Section 1107.8, on each inlet of each liquid receiver. Stop valves shall not be required on the inlet ...
Mechanical Code 2018 of Maryland > 11 Refrigeration > 1107 Refrigerant Piping > 1107.8 Stop Valves > 1107.8.1 Liquid Receivers
3.3.34 Definitions, Bulk Plant or Terminal
That portion of a property where liquids are received by tank vessel, pipelines, tank car, or tank vehicle and are stored or blended in bulk ...
State of Maryland Fire Prevention Code > 3 Definitions > 3.3 General Definitions > 3.3.34 Bulk Plant or Terminal
Class II or Class IIIA liquids shall have the receiving end of the fill pipe securely connected to a deck plate and fitted with a screw cap. Such ...
State of Maryland Fire Prevention Code > 42 Refueling > 42.9 Marine Fueling > 42.9.10 Operating Requirements > 220.127.116.11
502.9.5.5 Exhaust Systems, Bulk Plants or Terminals
Ventilation shall be provided for portions of properties where flammable and combustible liquids are received by tank vessels, pipelines, tank cars ...
Mechanical Code 2018 of Maryland > 5 Exhaust Systems > 502 Required Systems > 502.9 Hazardous Materials—Requirements for Specific Materials > 502.9.5 Flammable and Combustible Liquids > 502.9.5.5 Bulk Plants or Terminals
301.3 General Regulations, Connections to Drainage System
Plumbing fixtures, drains, appurtenances and appliances used to receive or discharge liquid waste or sewage shall be directly connected ...
Plumbing Code 2018 of Maryland > 3 General Regulations > 301 General > 301.3 Connections to Drainage System