// CODE SNIPPET
C405.5.1.4 Line-Voltage Lighting Track and Plug-In Busway
JUMP TO FULL CODE CHAPTER
The wattage shall be:
- The specified wattage of the luminaires included in the system with a minimum of 30 W/lin ft. (98 W/lin. m);
- The wattage limit of the system's circuit breaker; or
- The wattage limit of other permanent current limiting device(s) on the system.
Related Code Sections
C405.5.1.4 [CE] Commercial Energy Efficiency, Line-Voltage Lighting Track and Plug-In Busway
The wattage shall be: The specified wattage of the luminaires included in the system with a minimum of 30 W/lin ft. (98 W/lin. m); The wattage ...
DC Energy Conservation Code 2013 > 4 [CE] Commercial Energy Efficiency > C405 Electrical Power and Lighting Systems (Mandatory) > C405.5 Interior Lighting Power Requirements (Prescriptive) > C405.5.1 Total Connected Interior Lighting Power > C405.5.1.4 Line-Voltage Lighting Track and Plug-In Busway
Section E4005 Devices and Luminaires, Track Lighting
Lighting track shall be permanently installed and permanently connected to a branch circuit having a rating not more than that of the track ...
E4207.3 Swimming Pools, Luminaires
A luminaire installed in or on the wall of a storable pool shall be part of a cord and plug-connected lighting assembly ...
E3909.4 Power and Lighting Distribution, Attachment Plugs
Where used in accordance with Section E3909.1, each flexible cord shall be equipped with an attachment plug and shall be energized from a receptacle ...
DC Residential Code 2013 > 39 Power and Lighting Distribution > E3909 Flexible Cords > E3909.4 Attachment Plugs
E3702.1 Branch Circuit and Feeder Requirements, Branch-Circuit Voltage Limitations
The voltage ratings of branch circuits that supply luminaires or receptacles for cord-and-plug-connected loads of up to 1,400 volt-amperes or of less ...
DC Residential Code 2013 > 37 Branch Circuit and Feeder Requirements > E3702 Branch Circuit Ratings > E3702.1 Branch-Circuit Voltage Limitations