// CODE SNIPPET
184.108.40.206 Limited Access Structures (Nonsprinklered Buildings)
JUMP TO FULL CODE CHAPTER
Any one of the following means shall be provided to evacuate smoke from the smoke compartment of fire origin:
- Operable windows on not less than two sides of the building, spaced not more than 30 ft (9.1 m) apart, that provide openings with dimensions of not less than 22 in. (560 mm) in width and 24 in. (610 mm) in height
- *Manual or automatic smoke vents
- Engineered smoke control system
- Mechanical exhaust system providing not less than six air changes per hour
- Other method acceptable to the authority having jurisdiction
Related Code Sections
220.127.116.11 New Detention and Correctional Occupancies, Limited Access Structures (Nonsprinklered Buildings)
Limited access structures used as detention and correctional occupancies shall comply with 18.104.22.168.2. The provisions of Section 11.7 for limited ...
Life Safety Code 2018 of Kansas > 22 New Detention and Correctional Occupancies > 22.4 Special Provisions > 22.4.4 Nonsprinklered Existing Building Renovations > 22.214.171.124 Limited Access Structures (Nonsprinklered Buildings)
3805.2 Higher Education Laboratories, Nonsprinklered Laboratories
at 25 percent of Table 5003.1.1(1) limits for a building equipped throughout with an automatic sprinkler system . Pyrophorics. Class 4 Oxidizers ...
Fire Code 2018 of Kansas > 38 Higher Education Laboratories > 3805 Nonsprinklered Laboratories > 3805.2 Nonsprinklered Laboratories
126.96.36.199.3 Special Structures and High-Rise Buildings, Nonsprinklered Towers
The levels located within a tower below the observation level and the equipment room for that level in nonsprinklered towers shall not be occupied ...
Life Safety Code 2018 of Kansas > 11 Special Structures and High-Rise Buildings > 11.3 Towers > 11.3.1 Application > 188.8.131.52 Use of Accessory Levels > 184.108.40.206.3 Nonsprinklered Towers
3220.127.116.11 High-Piled Combustible Storage, Nonsprinklered Buildings
Aisles in nonsprinklered buildings shall be not less than 96 inches (2438 mm) wide ...
Fire Code 2018 of Kansas > 32 High-Piled Combustible Storage > 3206 General Fire Protection and Life Safety Features > 3206.10 Aisles > 3206.10.1 Width > 318.104.22.168 Nonsprinklered Buildings