// CODE SNIPPET
1101.16 Leaders, Conductors, and Connections
JUMP TO FULL CODE CHAPTER
The sanitary and storm drainage system of a building shall be entirely separate, except where a combined sewer is used, in which case the building storm drain shall be connected in the same horizontal plane through a single wye fitting to the combined building sewer not less than 10 feet (3048 mm) downstream from a soil stack.
Related Code Sections
1101.16 Storm Drainage, Leaders, Conductors, and Connections
Leaders or conductors shall not be used as soil, waste, or vent pipes nor shall soil, waste, or vent pipes be used as leaders or conductors ...
2018 Uniform Plumbing Code of Nevada > 11 Storm Drainage > 1101.0 General > 1101.16 Leaders, Conductors, and Connections
1101.15 Storm Drainage, Traps on Storm Drains and Leaders
Leaders and storm drains, where connected to a combined sewer, shall be trapped. Floor and area drains connected to a storm drain shall be trapped ...
2018 Uniform Plumbing Code of Nevada > 11 Storm Drainage > 1101.0 General > 1101.15 Traps on Storm Drains and Leaders
1101.0 Storm Drainage, General
leaders and conductors connected to a building storm sewer shall have a cleanout installed at the base of the outside leader or outside conductor before ...
1103.1 Storm Drainage, Vertical Conductors and Leaders
Vertical conductors and leaders shall be sized by the maximum projected roof area and Table 1103.1. TABLE 1103.1 SIZING ROOF DRAINS, LEADERS, AND ...
2018 Uniform Plumbing Code of Nevada > 11 Storm Drainage > 1103.0 Size of Leaders, Conductors, and Storm Drains > 1103.1 Vertical Conductors and Leaders
K 106.6 Potable Rainwater Catchment Systems, Drains, Conductors, and Leaders
The design and size of rainwater drains, conductors, and leaders shall comply with this code ...
2018 Uniform Plumbing Code of Nevada > K Potable Rainwater Catchment Systems > K 106.0 Water Quality Devices and Equipment > K 106.6 Drains, Conductors, and Leaders