// CODE SNIPPET
(D) Large Wire or Factory Connections
JUMP TO FULL CODE CHAPTER
For motors with larger ratings, greater number of leads, or larger wire sizes, or where motors are installed as a part of factory-wired equipment, without additional connection being required at the motor terminal housing during equipment installation, the terminal housing shall be of ample size to make connections, but the foregoing provisions for the volumes of terminal housings shall not be considered applicable.
Related Code Sections
(D) Equipment for General Use, Large Wire or Factory Connections
For motors with larger ratings, greater number of leads, or larger wire sizes, or where motors are installed as a part of factory-wired equipment ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 430 Motors, Motor Circuits, and Controllers > 430.12 Motor Terminal Housings > (D) Large Wire or Factory Connections
240.8 Wiring and Protection, Fuses or Circuit Breakers in Parallel
Fuses and circuit breakers shall be permitted to be connected in parallel where they are factory assembled in parallel and listed as a unit ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 240 Overcurrent Protection > 240.8 Fuses or Circuit Breakers in Parallel
300.40 Wiring Methods and Materials, Insulation Shielding
, wires, or braids, or combinations thereof, shall be connected to an equipment grounding conductor, an equipment grounding busbar, or a grounding ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 300 General Requirements for Wiring Methods and Materials > 300.40 Insulation Shielding
(1) Wiring Methods and Materials, Large Equipment
Boxes that enclose devices or utilization equipment that projects more than 48 mm (1 7 / 8 in.) rearward from the mounting plane of the box shall ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 314 Outlet, Device, Pull, and Junction Boxes; Conduit Bodies; Fittings; And Handhole Enclosures > 314.24 Depth of Boxes > (B) Outlet and Device Boxes With Enclosed Devices or Utilization Equipment > (1) Large Equipment
(C) Special Occupancies, Wiring Requirements
The life safety branch and critical branch [of the essential electrical system] shall be kept independent of all other wiring and equipment. [ 99 ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.31 Requirements for the Essential Electrical System > (C) Wiring Requirements