// CODE SNIPPET
G2415.10 (404.10) Isolation
JUMP TO FULL CODE CHAPTER
Metallic piping and metallic tubing that conveys fuel gas from an LP-gas storage container shall be provided with an approved dielectric fitting to electrically isolate the underground portion of the pipe or tube from the above ground portion that enters a building. Such dielectric fitting shall be installed above ground outdoors.
Related Code Sections
G2415.10 Fuel Gas, (404.10) Isolation
fitting to electrically isolate the underground portion of the pipe or tube from the above ground portion that enters a building. Such dielectric fitting ...
2015 Michigan Residential Code > 24 Fuel Gas > G2415 (404) Piping System Installation > G2415.10 (404.10) Isolation
404.10 Special Detailed Requirements Based on Use and Occupancy, Interior Exit Stairways
A maximum of 50 percent of interior exit stairways are permitted to egress through an atrium on the level of exit discharge in accordance ...
2015 Michigan Building Code > 4 Special Detailed Requirements Based on Use and Occupancy > 404 Atriums > 404.10 Interior Exit Stairways
E4001.10 Devices and Luminaires, Box Mounted
or part of listed assemblies or systems, in accordance with the manufacturer's instructions. [404.10(B)] ...
301.13 General Regulations, Vibration Isolation
Where vibration isolation of equipment and appliances is employed, an approved means of supplemental restraint shall be used to accomplish ...
506.3.2.4 Exhaust Systems, Vibration Isolation
A vibration isolation connector for connecting a duct to a fan shall consist of noncombustible packing in a metal sleeve joint of approved design ...
2015 Michigan Mechanical Code > 5 Exhaust Systems > 506 Commercial Kitchen Hood Ventilation System Ducts and Exhaust Equipment > 506.3 Ducts Serving Type I Hoods > 506.3.2 Joints, Seams and Penetrations of Grease Ducts > 506.3.2.4 Vibration Isolation