// CODE SNIPPET
(B) Isolated Grounding Circuits
JUMP TO FULL CODE CHAPTER
Where installed for the reduction of electromagnetic interference on the grounding circuit, an equipment enclosure supplied by a branch circuit shall be permitted to be isolated from a raceway containing circuits supplying only that equipment by one or more listed nonmetallic raceway fittings located at the point of attachment of the raceway to the equipment enclosure. The metal raceway shall comply with this article and shall be supplemented by an internal insulated equipment grounding conductor installed in accordance with 250.146(D) to ground the equipment enclosure.
Related Code Sections
(B) Wiring and Protection, Isolated Grounding Circuits
Where installed for the reduction of electromagnetic interference on the grounding circuit, an equipment enclosure supplied by a branch circuit shall ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 250 Grounding and Bonding > 250.96 Bonding Other Enclosures > (B) Isolated Grounding Circuits
(C) Special Equipment, Bipolar Source and Output Circuits
fault or arc fault, the monopole subarray circuits shall be isolated from ground ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 690 Solar Photovoltaic (PV) Systems > 690.7 Maximum Voltage > (C) Bipolar Source and Output Circuits
(1) Special Occupancies,
The equipment grounding terminals of isolated ground receptacles installed in branch circuits for patient care spaces shall be connected ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.16 Use of Isolated Ground Receptacles > (B) Outside of a Patient Care Vicinity > (1)
(B) Special Equipment, Secondary-Circuit Ground-Fault Protection
Transformers and electronic power supplies other than the following shall have secondary-circuit ground-fault protection: Transformers ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 600 Electric Signs and Outline Lighting > 600.23 Transformers and Electronic Power Supplies > (B) Secondary-Circuit Ground-Fault Protection
(4) Special Occupancies, Bonding Provisions
The site-isolating device enclosure shall be connected to the grounded circuit conductor and the grounding electrode system ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 547 Agricultural Buildings > 547.9 Electrical Supply to Building(s) or Structure(s) From a Distribution Point > (A) Site-Isolating Device > (4) Bonding Provisions