// CODE SNIPPET
(1) Isolated Equipment Grounding Conductor Required
Related Code Sections
(1) Equipment for General Use, Isolated Equipment Grounding Conductor Required
Receptacles so identified shall be used only with equipment grounding conductors that are isolated in accordance with 250.146(D) ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 406 Receptacles, Cord Connectors, and Attachment Plugs (Caps) > 406.3 Receptacle Rating and Type > (D) Isolated Ground Receptacles > (1) Isolated Equipment Grounding Conductor Required
(B) Wiring and Protection, Isolated Grounding Circuits
: Use of an isolated equipment grounding conductor does not relieve the requirement for grounding the raceway system ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 250 Grounding and Bonding > 250.96 Bonding Other Enclosures > (B) Isolated Grounding Circuits
(H) Special Occupancies, Special-Purpose Receptacle Grounding
ungrounded system, the equipment grounding conductor shall not be required to be run with the power conductors; however, the equipment grounding terminal ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.19 Category 1 (Critical Care) Spaces > (H) Special-Purpose Receptacle Grounding
(B) Special Equipment, Isolated Ground Receptacles
Isolated ground receptacles shall be permitted as described in 250.146(D); however, the branch-circuit equipment grounding conductor shall ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 647 Sensitive Electronic Equipment > 647.7 Receptacles > (B) Isolated Ground Receptacles
(D) Wiring and Protection, Connection to Ground
Isolating switches shall be provided with a means for readily connecting the load side conductors to a grounding electrode system, equipment ground ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 230 Services > 230.204 Isolating Switches > (D) Connection to Ground