// CODE SNIPPET
188.8.131.52.2 Irregular Areas
JUMP TO FULL CODE CHAPTER
Related Code Sections
184.108.40.206.2 Initiating Devices, Irregular Areas
For irregularly shaped areas, the spacing between detectors shall be permitted to be greater than the listed spacing, provided that the maximum ...
National Fire Alarm and Signaling Code 2019 of Maine > 17 Initiating Devices > 17.6 Heat-Sensing Fire Detectors > 17.6.3 Location and Spacing > 220.127.116.11 Smooth Ceiling > 18.104.22.168.2 Irregular Areas
22.214.171.124.3 Installation Requirements,
Where walls are angled or irregular, the maximum horizontal distance between a sprinkler and any point of floor area protected by that sprinkler ...
Standard for the Installation of Sprinkler Systems 2016 of Maine > 8 Installation Requirements > 8.8 Extended Coverage Upright and Pendent Spray Sprinklers > 8.8.3 Sprinkler Spacing (Extended Coverage Upright and Pendent Spray Sprinklers) > 126.96.36.199 Maximum Distance From Walls > 188.8.131.52.3
184.108.40.206.3* Installation Requirements,
The requirements of 220.127.116.11.1 shall not apply where walls are angled or irregular, and the maximum horizontal distance between a sprinkler and any ...
Standard for the Installation of Sprinkler Systems 2016 of Maine > 8 Installation Requirements > 8.6 Standard Pendent and Upright Spray Sprinklers > 8.6.3 Sprinkler Spacing (Standard Pendent and Upright Spray Sprinklers) > 18.104.22.168 Maximum Distance From Walls > 22.214.171.124.3*
R301.2.2.2.5 Building Planning, Irregular Buildings
The seismic provisions of this code shall not be used for irregular structures located in Seismic Design Categories C, D 0 , D 1 and D 2 . Irregular ...
Residential Building Code of the MUBEC and MUBC > 3 Building Planning > R301 Design Criteria > R301.2 Climatic and Geographic Design Criteria > R301.2.2 Seismic Provisions > R301.2.2.2 Seismic Design Category C > R301.2.2.2.5 Irregular Buildings
126.96.36.199.3 Flammable and Combustible Liquids,
Where tanks are in a diked area containing Class I or Class II liquids or in the drainage path of Class I or Class II liquids and are compacted ...
Fire Code 2018 of Maine > 66 Flammable and Combustible Liquids > 66.22 Storage of Liquids in Tanks — Aboveground Storage Tanks > 66.22.4* Location of Aboveground Storage Tanks > 188.8.131.52 Shell-To-Shell Spacing of Adjacent Aboveground Storage Tanks > 184.108.40.206.3