// CODE SNIPPET
1109.1.3 Iron and Steel
Related Code Sections
1109.1.3 Refrigeration, Iron and Steel
Iron and steel refrigeration piping, valves, fittings, and related parts shall be approved for the intended use. Pipe exceeding 2 inches (50 mm) iron ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1109.0 Refrigeration Piping, Containers, and Valves > 1109.1 Materials > 1109.1.3 Iron and Steel
10.6.2.1.4.1 Underground Requirements,
Washers shall be permitted to be cast iron or steel and round or square. [ 24: 10.6.2.1.4.1] ...
Standard for the Installation of Sprinkler Systems 2016 of Nevada > 10 Underground Requirements > 10.6* Restraint > 10.6.2* Restrained Joint Systems > 10.6.2.1 Sizing Clamps, Rods, Bolts, and Washers > 10.6.2.1.4 Washers > 10.6.2.1.4.1
310.8 General Regulations, Screwed Fittings
Screwed fittings shall be ABS, cast-iron, copper, copper alloy, malleable iron, PVC, steel, or other approved materials. Threads shall be tapped out ...
2018 Uniform Plumbing Code of Nevada > 3 General Regulations > 310.0 Prohibited Fittings and Practices > 310.8 Screwed Fittings
F 801.4 Firefighter Breathing Air Replenishment Systems, Prohibited Materials
The use of nonmetallic materials, carbon steel, iron pipe, malleable iron, high-strength gray iron, or alloy steel shall be prohibited for breathing ...
2018 Uniform Plumbing Code of Nevada > F Firefighter Breathing Air Replenishment Systems > F 801.0 Materials > F 801.4 Prohibited Materials
220.127.116.11.3 Public Emergency Alarm Reporting Systems,
Single wire shall meet IMSA specifications and shall not be smaller than No. 10 Roebling gauge if of galvanized iron or steel; 10 AWG if of hard ...
National Fire Alarm and Signaling Code 2016 of Nevada > 27 Public Emergency Alarm Reporting Systems > 27.7 Public Cable Plant > 27.7.1 Requirements for Metallic and Fiber-Optic Systems — Metallic and Fiber-Optic Interconnections > 18.104.22.168 Aerial Construction > 22.214.171.124.3