// CODE SNIPPET
604.13 Internal Insulation
JUMP TO FULL CODE CHAPTER
Materials used as internal insulation and exposed to the airstream in ducts shall be shown to be durable when tested in accordance with UL 181. Exposed internal insulation that is not impermeable to water shall not be used to line ducts or plenums from the exit of a cooling coil to the downstream end of the drain pan.
Related Code Sections
604.13 Duct Systems, Internal Insulation
Materials used as internal insulation and exposed to the airstream in ducts shall be shown to be durable when tested in accordance with UL 181 ...
Section 1204 Hydronic Piping, Pipe Insulation
Pipe insulation installed in buildings shall conform to the requirements of the International Energy Conservation Code ; shall be tested ...
602.2.1.6 Duct Systems, Foam Plastic Insulation
insulation shall be separated from the plenum by a thermal barrier complying with Section 2603.4 of the International Building Code and shall exhibit ...
2015 Michigan Mechanical Code > 6 Duct Systems > 602 Plenums > 602.2 Construction > 602.2.1 Materials Within Plenums > 602.2.1.6 Foam Plastic Insulation
718.5 Fire and Smoke Protection Features, Combustible Materials in Concealed Spaces in Type I or II Construction
with the International Mechanical Code and the International Plumbing Code. Combustible insulation and covering on pipe and tubing, installed in concealed ...
2015 Michigan Building Code > 7 Fire and Smoke Protection Features > 718 Concealed Spaces > 718.5 Combustible Materials in Concealed Spaces in Type I or II Construction
607.5 Water Supply and Distribution, Insulation of Piping
conveying water heated by a water heater shall be insulated in accordance with Section R403.5.3 of the International Energy Conservation Code ...
2015 Michigan Plumbing Code > 6 Water Supply and Distribution > 607 Hot Water Supply System > 607.5 Insulation of Piping