// CODE SNIPPET
188.8.131.52.2* Internal Dispenser Cabinet Inspection
JUMP TO FULL CODE CHAPTER
An inspection of the fuel dispensing equipment that is located inside the dispenser cabinet shall be conducted. The interior of the fuel dispenser cabinet shall be inspected for signs of leaks, damage, corrosion, or weathering, with particular attention to the sump area and joints and castings of fluid handling components. The inspection shall be conducted at least monthly and shall be documented. Documentation shall be available for review by the AHJ upon request. [30A:184.108.40.206]
Related Code Sections
220.127.116.11.2* Refueling, Internal Dispenser Cabinet Inspection
An inspection of the fuel dispensing equipment that is located inside the dispenser cabinet shall be conducted. The interior of the fuel dispenser ...
Fire Code 2018 of West Virginia > 42 Refueling > 42.5 Fuel Dispensing Systems > 42.5.3 Requirements for Dispensing Devices > 18.104.22.168 Inspections > 22.214.171.124.2* Internal Dispenser Cabinet Inspection
502.9.8 Exhaust Systems, Highly Toxic and Toxic Compressed Gases— Quantities Exceeding the Maximum Allowable Quantity Per Control Area
The room or area in which indoor gas cabinets or exhausted enclosures are located shall be provided with exhaust ventilation. Gas cabinets ...
Mechanical Code 2015 of West Virginia > 5 Exhaust Systems > 502 Required Systems > 502.9 Hazardous Materials—Requirements for Specific Materials > 502.9.8 Highly Toxic and Toxic Compressed Gases— Quantities Exceeding the Maximum Allowable Quantity Per Control Area
63.2.17 Compressed Gases and Cryogenic Fluids, Gas Cabinets
Where a gas cabinet is required, is used to provide separation of gas hazards, or is used to increase the threshold quantity for a gas requiring ...
Fire Code 2018 of West Virginia > 63 Compressed Gases and Cryogenic Fluids > 63.2 Building-Related Controls > 63.2.17 Gas Cabinets
126.96.36.199.3.10 Fire Protection Systems, Cabinets
Cabinets housing fire extinguishers shall not be locked, except where fire extinguishers are subject to malicious use and cabinets include a means ...
Fire Code 2018 of West Virginia > 13 Fire Protection Systems > 13.6 Portable Fire Extinguishers > 13.6.3 Installation of Portable Fire Extinguishers > 188.8.131.52 General > 184.108.40.206.3 Placement > 220.127.116.11.3.10 Cabinets
18.104.22.168.8.1 Refueling, Cabinets
All cabinets, other than those housing electronic equipment, shall be vented to prevent the accumulation of fuel vapors. (See 22.214.171.124.6.) [ 407 ...
Fire Code 2018 of West Virginia > 42 Refueling > 42.10 Aircraft Fuel Servicing > 42.10.4 Airport Fueling Vehicles > 126.96.36.199 Design and Construction > 188.8.131.52.8 Filters and Ancillary Equipment > 184.108.40.206.8.1 Cabinets