// CODE SNIPPET
704.1.2.3.2 Interior Piping
Related Code Sections
704.1.2.3.2 Gaseous Hydrogen Systems, Interior Piping
Except for through penetrations, piping located inside of buildings shall be installed in exposed locations and provided with ready access ...
Fuel Gas Code 2018 of Kansas > 7 Gaseous Hydrogen Systems > 704 (IFGC) Piping, Use and Handling > 704.1 Applicability > 704.1.2 Piping Systems > 704.1.2.3 Piping Design and Construction > 704.1.2.3.2 Interior Piping
E3608.1.1.1 Services, Interior Metal Water Piping
Interior metal water piping located more than 5 feet (1524 mm) from the point of entrance into the building shall not be used as a conductor ...
Residential Code 2018 of Kansas > 36 Services > E3608 Grounding Electrode System > E3608.1 Grounding Electrode System > E3608.1.1 Metal Underground Water Pipe > E3608.1.1.1 Interior Metal Water Piping
E3611.4 Services, Interior Metal Water Piping
Where grounding electrode conductors and bonding jumpers are connected to interior metal water piping as a means to extend the grounding electrode ...
Residential Code 2018 of Kansas > 36 Services > E3611 Grounding Electrode Conductor Connection to the Grounding Electrodes > E3611.4 Interior Metal Water Piping
(1) Wiring and Protection, Continuity
Continuity of the grounding path or the bonding connection to interior piping shall not rely on water meters or filtering devices and similar ...
National Electrical Code 2017 of Kansas > 2 Wiring and Protection > 250 Grounding and Bonding > 250.53 Grounding Electrode System Installation > (D) Metal Underground Water Pipe > (1) Continuity
26.8.1 Marine Systems, Hydrostatic Tests
In addition to the interior piping, the test required by 18.104.22.168 shall also be conducted on all external water supply connections including ...
Standard for the Installation of Sprinkler Systems 2016 of Kansas > 26 Marine Systems > 26.8 System Acceptance > 26.8.1 Hydrostatic Tests