// CODE SNIPPET
722.214.171.124 Interior Fire Window Assemblies
JUMP TO FULL CODE CHAPTER
Fire-protection-rated glazing requiring 45-minute opening protection in accordance with Table 716.1(3) shall be limited to fire partitions designed in accordance with Section 708 and fire barriers utilized in the applications set forth in Sections 707.3.6, 707.3.7 and 707.3.9 where the fire-resistance rating does not exceed 1 hour. Fire-resistance-rated glazing assemblies tested in accordance with ASTM E119 or UL 263 shall not be subject to the limitations of this section.
The total area of the glazing in fire-protection-rated window assemblies shall not exceed 25 percent of the area of a common wall with any room.
Related Code Sections
7126.96.36.199 Fire and Smoke Protection Features, Interior Fire Window Assemblies
Fire-protection-rated glazing used in fire window assemblies located in fire partitions and fire barriers shall be limited to use in assemblies ...
Building Code 2018 of Illinois > 7 Fire and Smoke Protection Features > 716 Opening Protectives > 716.3 Fire Window Assemblies > 716.3.2 Performance Requirements > 7188.8.131.52 Interior Fire Window Assemblies
707.6 Fire and Smoke Protection Features, Openings
-resistance rating of the wall. Fire window assemblies permitted in atrium separation walls shall not be limited to a maximum aggregate width of 25 ...
Building Code 2018 of Illinois > 7 Fire and Smoke Protection Features > 707 Fire Barriers > 707.6 Openings
427.2 Special Detailed Requirements Based on Occupancy and Use, Interior Supply Location
Openings between the room or enclosure and interior spaces shall be provided with self-closing smoke- and draft-control assemblies having a fire ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 427 Medical Gas Systems > 427.2 Interior Supply Location
802.6 Interior Finishes, Windows
Show windows in the exterior walls of the first story above grade plane shall be permitted to be of wood or of unprotected metal framing ...
7184.108.40.206 Fire and Smoke Protection Features, Fire Window Frames
Fire window frames shall be approved for the intended application ...
Building Code 2018 of Illinois > 7 Fire and Smoke Protection Features > 716 Opening Protectives > 716.3 Fire Window Assemblies > 716.3.5 Labeled Protective Assemblies > 7220.127.116.11 Fire Window Frames