// CODE SNIPPET
1208.3 Interconnections Between Gas Piping Systems
Go To Full Code Chapter
Where two or more meters, or two or more service regulators where meters are not provided, are located on the same premises and supply separate users, the gas piping systems shall not be interconnected on the outlet side of the meters or service regulators. [NFPA 54:5.3.1]
1208.3.1 Interconnections for Standby Fuels
Where a supplementary gas for standby use is connected downstream from a meter or a service regulator where a meter is not provided, equipment to prevent backflow shall be installed. A three-way valve installed to admit the standby supply and at the same time shut off the regular supply shall be permitted to be used for this purpose. [NFPA 54:22.214.171.124 — 126.96.36.199]
Related Code Sections
1208.3 Fuel Gas Piping, Interconnections Between Gas Piping Systems
, the gas piping systems shall not be interconnected on the outlet side of the meters or service regulators. [NFPA 54:5.3.1 ...
1323.7 Health Care Facilities and Medical Gas and Medical Vacuum Systems, Prohibited System Interconnections
Two or more medical gas or vacuum piping systems shall not be interconnected for installation, testing, or any other reason except as permitted ...
G2412.6 Fuel Gas, (401.6) Interconnections
Where two or more meters are installed on the same premises but supply separate consumers, the piping systems shall not be interconnected ...
242.54 Wiring and Protection, Interconnections
The surge arrester protecting a transformer that supplies a secondary distribution system shall be interconnected as specified in 242.54(A), (B ...
(D) Special Conditions, Unbalanced Interconnections
Unbalanced ac connections between an ESS and other ac electric power production sources shall be in accordance with 705.45 ...