// CODE SNIPPET
[F] 907.2.10.4 Installation Near Bathrooms
Related Code Sections
907.2.10.4 Fire Protection and Life Safety Systems, Installation Near Bathrooms
Smoke alarms shall be installed not less than 3 feet (914 mm) horizontally from the door or opening of a bathroom that contains a bathtub or shower ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 907 Fire Alarm and Detection Systems > 907.2 Where Required—New Buildings and Structures > 907.2.10 Single- And Multiple-Station Smoke Alarms > 907.2.10.4 Installation Near Bathrooms
18.104.22.168 Scoping Requirements, Toilet Facilities
If toilets are required in the facility by the Illinois Plumbing Code , at least one accessible toilet room for each sex shall be provided as near ...
2018 Illinois Accessibility Code > 2 Scoping Requirements > 202 Existing Buildings and Facilities > 202.5 Alterations to Qualified Historic Buildings and Facilities > 202.5.2 Alterations to Historically Interpreted Buildings > 22.214.171.124 Toilet Facilities
(D) Wiring and Protection, Bathrooms
At least one receptacle outlet shall be installed in bathrooms within 900 mm (3 ft) of the outside edge of each basin. The receptacle outlet shall ...
National Electrical Code 2017 of Illinois > 2 Wiring and Protection > 210 Branch Circuits > 210.52 Dwelling Unit Receptacle Outlets > (D) Bathrooms
(2) Wiring and Protection, Bathrooms
Service disconnecting means shall not be installed in bathrooms ...
National Electrical Code 2017 of Illinois > 2 Wiring and Protection > 230 Services > 230.70 General > (A) Location > (2) Bathrooms
807.3 Alterations—Level 2, Residential Occupancies
than one duplex receptacle outlet located near the laundry equipment and installed on an independent circuit ...
Existing Building Code 2018 of Illinois > 8 Alterations—Level 2 > 807 Electrical > 807.3 Residential Occupancies