// CODE SNIPPET
1306.3 Inside Tanks
JUMP TO FULL CODE CHAPTER
Related Code Sections
1306.3 Fuel Oil Piping and Storage, Inside Tanks
The gauging of inside tanks by means of measuring sticks shall not be permitted. An inside tank provided with fill and vent pipes shall be provided ...
2015 Michigan Mechanical Code > 13 Fuel Oil Piping and Storage > 1306 Oil Gauging > 1306.3 Inside Tanks
M2201.5 Special Piping and Storage Systems, Oil Gauges
Inside tanks shall be provided with a device to indicate when the oil in the tank has reached a predetermined safe level. Glass gauges or a gauge ...
2015 Michigan Residential Code > 22 Special Piping and Storage Systems > M2201 Oil Tanks > M2201.5 Oil Gauges
1307.1 Fuel Oil Piping and Storage, Building Shutoff
A shutoff valve shall be installed on the fuel-oil supply line at the entrance to the building. Inside or above-ground tanks are permitted to have ...
2015 Michigan Mechanical Code > 13 Fuel Oil Piping and Storage > 1307 Fuel Oil Valves > 1307.1 Building Shutoff
418.4 Special Detailed Requirements Based on Use and Occupancy, Tank Storage
Storage areas for flammable and combustible liquid tanks inside of structures shall be located at or above grade and shall be separated from ...
2015 Michigan Building Code > 4 Special Detailed Requirements Based on Use and Occupancy > 418 Organic Coatings > 418.4 Tank Storage