JUMP TO FULL CODE CHAPTER
- If the ambient infra-red light (generally caused by other infra-red light-generating devices or direct sunlight) produces interference, it is recommended that, unless the interfering infra-red light can be reduced, infra-red systems not be considered.
- Given an input signal to the transmitter at the levels specified in Item 6 over a minimum frequency range of 200 Hz to 8,000 Hz, the measured frequency response of the output signal generated by the receiver and transducer over that range shall not vary by more than +/- 5 decibels from the value at 1,000 Hz. In actual usage, graphic equalization of the output signal is allowed.
- Given an input signal to the transmitter at the levels specified in Item 6, the minimum signal-to-noise ratio of the output generated by the receiver and transducer shall be 35 decibels at all frequencies specified in Item 2.
- Given an input signal of 1,000 Hz to the transmitter at a level sufficient to produce the minimum signal-to-noise ratio specified in Item 3, the harmonic distortion produced by the receiver and transducer shall not be more than 5 percent.
- Given a 1,000 Hz sinusoidal input signal at the levels specified in Item 6, the following are the possible transducers:
- If using a neckloop as an output transducer, generate a magnetic field strength of at least 150 mA/meter. The peak field strength shall not exceed 600 mA/meter. Measurements shall be made at the geometric center of the plane of the neckloop.
- If using a silhouette as an output transducer, generate a magnetic field strength of at least 50 mA/meter (the peak field strength shall not exceed 200 mA/meter). Measurements shall be made at a distance of 10 centimeters from the silhouette.
- If using a miniature earphone as an output transducer, generate a sound pressure level of at least 80 decibels. The maximum high-frequency average sound pressure level shall not exceed 130 decibels.
- If a direct input cable is used between the output of the receiver and the input of a hearing aid boot or shoe, generate a minimum voltage range of 2 mV to 800 mV and match a boot/shoe input impedance of 50 ohms or greater. The plugs at either end shall be molded 2-pin, 3-pin and/or 3.5-millimeter mini-plug (stereo or mono).
- The system must have inputs capable of accepting signals at line level and microphone level and must be capable of interfacing with existing public address systems or stand-alone.
- The minimum light level of the transmitted infra-red carrier signal must be sufficient so that a receiver can produce the specifications in Items 2, 3, 4 and 5 at any point within the user area.
- Any stand-alone devices powered by 110‒120 volt AC used as part of the system must be tested by an approved laboratory.
- All input wiring must comply with the New York City Electrical Code.
- The installation of all stand-alone components of the system must comply with the New York City Electrical Code.
Related Code Sections
, it is recommended that, unless the interfering infra-red light can be reduced, infra-red systems not be considered. 2. Given an input signal ...
, it is recommended that, unless the interfering infra-red light can be reduced, infra-red systems not be considered. Given an input signal ...
be painted red and the handles of valves serving such combination system shall be painted yellow ...
system in new buildings, including buildings constructed pursuant to Section 28-101.4.2 of the Administrative Code , shall be painted red prior ...
Manual fire alarm boxes shall be red in color ...
Calculate Code Requirements
Code Calculators automatically generate a detailed list of requirements.
Upgrade to premium to access these features.
UpCodes provides an intuitive resource to navigate building regulations.
Codes are organized by jurisdiction to help you understand which regulations apply to your project.
Find Your Codes