// CODE SNIPPET
[F] 413.4.3 Indoor Installation
JUMP TO FULL CODE CHAPTER
A residential fueling appliance installed indoors or used for indoor fueling shall comply with all of the following:
- The capacity shall not exceed 5 cubic feet per minute (0.14 m3/min) of natural gas.
- Fuel gas from the pressure relief and blowdown systems shall be vented to the outdoors.
- A methane gas detector shall be installed in the room or space containing the appliance or where fueling occurs and shall be located not lower than 6 inches (152 mm) from the highest point in the room or space. The detector shall be set to activate at onefifth of the lower limit of flammability of natural gas and shall be interlocked with the residential fuel appliance to stop or prevent its operation upon activation. The detector shall have an audible or visible alarm.
- The capacity of a residential fueling appliance installed outdoors for outdoor fueling shall not exceed 10 feet cubic per minute (0.28 m3/min) of natural gas. Residential fueling appliances located outdoors shall be installed on a firm, noncombustible base.
Related Code Sections
(B) General, Indoor Installations
Indoor electrical installations that are accessible to unqualified persons shall be made with metal-enclosed equipment. Switchgear, transformers ...
National Electrical Code 2017 of Kansas > 1 General > 110 Requirements for Electrical Installations > 110.31 Enclosure for Electrical Installations > (B) Indoor Installations
1205.6 Energy Systems, Indoor Installations
Stationary fuel cell power systems installed in indoor locations shall comply with Sections 1205.6 through 1205.6.2. For purposes of this section ...
Fire Code 2018 of Kansas > 12 Energy Systems > 1205 Stationary Fuel Cell Power Systems > 1205.6 Indoor Installations
413.4.3 Gas Piping Installations, Indoor Installation
A residential fueling appliance installed indoors or used for indoor fueling shall comply with all of the following: The capacity shall not exceed ...
Fuel Gas Code 2018 of Kansas > 4 Gas Piping Installations > 413 (IFGC) Compressed Natural Gas Motor Vehicle Fuel-Dispensing Facilities > 413.4 Residential Fueling Appliance Installation > 413.4.3 Indoor Installation
(A) Equipment for General Use, Indoor Installations
Indoor installations shall be permitted in accordance with one of the following: In Type I or Type II buildings, in areas where all ...
National Electrical Code 2017 of Kansas > 4 Equipment for General Use > 450 Transformers and Transformer Vaults (Including Secondary Ties) > 450.23 Less-Flammable Liquid-Insulated Transformers > (A) Indoor Installations
680.43 Special Equipment, Indoor Installations
A spa or hot tub installed indoors shall comply with the provisions of Parts I and II of this article except as modified by this section and shall ...
National Electrical Code 2017 of Kansas > 6 Special Equipment > 680 Swimming Pools, Fountains, and Similar Installations > 680.43 Indoor Installations