// CODE SNIPPET
E4203.1.6 Indoor GFCI Protection
Related Code Sections
E4203.1.6 Swimming Pools, Indoor GFCI Protection
All 125-volt receptacles rated 30 amperes or less and located within 10 feet (3048 mm) of the inside walls of spas and hot tubs installed indoors ...
Residential Code 2018 of Kansas > 42 Swimming Pools > E4203 Equipment Location and Clearances > E4203.1 Receptacle Outlets > E4203.1.6 Indoor GFCI Protection
(B) Wiring and Protection, Other Than Dwelling Units
other than those covered under 210.8(B)(1), GFCI protection shall not be required. Indoor wet locations Locker rooms with associated showering ...
National Electrical Code 2017 of Kansas > 2 Wiring and Protection > 210 Branch Circuits > 210.8 Ground-Fault Circuit-Interrupter Protection for Personnel > (B) Other Than Dwelling Units
(5) Equipment for General Use, GFCI Protection
Branch circuits supplying the heating panel or heating panel sets shall have ground-fault circuit-interrupter protection for personnel ...
National Electrical Code 2017 of Kansas > 4 Equipment for General Use > 424 Fixed Electric Space-Heating Equipment > 424.99 Installation Under Floor Covering > (B) Installation > (5) GFCI Protection
(F) Special Occupancies, GFCI Protection
All 125-volt, single-phase, 15- and 20-ampere receptacles shall have listed ground-fault circuit-interrupter protection for personnel. The GFCI ...
National Electrical Code 2017 of Kansas > 5 Special Occupancies > 551 Recreational Vehicles and Recreational Vehicle Parks > 551.71 Type Receptacles Provided > (F) GFCI Protection