// CODE SNIPPET
502.19 Indoor Firing Ranges
Related Code Sections
502.19 Exhaust Systems, Indoor Firing Ranges
Ventilation shall be provided in an approved manner in areas utilized as indoor firing ranges. Ventilation shall be designed to protect employees ...
Mechanical Code 2018 of Maryland > 5 Exhaust Systems > 502 Required Systems > 502.19 Indoor Firing Ranges
220.127.116.11.2 Marinas, Boatyards, Marine Terminals, Piers, and Wharves, Indoors
not be stored in an indoor boat storage area. [ 303: 18.104.22.168 ...
State of Maryland Fire Prevention Code > 28 Marinas, Boatyards, Marine Terminals, Piers, and Wharves > 28.1 Marinas, Boatyards, and Other Recreational Marine Facilities > 28.1.3 Berthing and Storage > 22.214.171.124 Dry Storage > 126.96.36.199.2 Indoors
188.8.131.52.1 Compressed Gases and Cryogenic Fluids, Indoors
The indoor storage or use of highly toxic gases or toxic gases shall be provided with a gas cabinet, exhausted enclosure, or gas room. [ 55: 184.108.40.206 ...
State of Maryland Fire Prevention Code > 63 Compressed Gases and Cryogenic Fluids > 63.3 Compressed Gases > 63.3.9 Toxic and Highly Toxic Gases > 220.127.116.11 Ventilation and Arrangement > 18.104.22.168.1 Indoors
22.214.171.124.1* Fire Protection Systems, Indoor Fire Pump Units
] Except as permitted in 126.96.36.199.1.3, indoor fire pump rooms in non-high ...
State of Maryland Fire Prevention Code > 13 Fire Protection Systems > 13.4 Fire Pumps > 13.4.2* Equipment Protection > 188.8.131.52* General Requirements > 184.108.40.206.1* Indoor Fire Pump Units
402.8.2.2 Special Detailed Requirements Based on Occupancy and Use, OLF Range
The occupant load factor ( OLF ) is not required to be less than 30 and shall not exceed 50 ...
Building Code 2018 of Maryland > 4 Special Detailed Requirements Based on Occupancy and Use > 402 Covered Mall and Open Mall Buildings > 402.8 Means of Egress > 402.8.2 Determination of Occupant Load > 402.8.2.2 OLF Range