// CODE SNIPPET
505.4 Indirect-Fired Water Heaters
JUMP TO FULL CODE CHAPTER
Indirect-fired water heaters shall be in accordance with the applicable sections of the ASME Boiler and Pressure Vessel Code or shall comply with one of the other applicable standards shown in Table 501.1(1). Each water heater shall bear a label in accordance with ASME requirements, or an approved testing agency, certifying and attesting that such an appliance has been tested, inspected and meets the requirements of the applicable standards or code.
An indirect-fired water heater that incorporates a single-wall heat exchanger shall be in accordance with the following requirements:
- The heat transfer medium shall be either potable water or contain fluids recognized as safe by the Food and Drug Administration (FDA) as food grade.
- Bear a label with the word "Caution," followed by the following statements:
- The word "Caution" and the statements in letters shall have an uppercase height of not less than 0.120 of an inch (3.048 mm). The vertical spacing between lines of type shall be not less than 0.046 of an inch (1.168 mm). Lowercase letters shall be compatible with the uppercase letter size specification.
Related Code Sections
505.4 Water Heaters, Indirect-Fired Water Heaters
Indirect-fired water heaters shall be in accordance with the applicable sections of the ASME Boiler and Pressure Vessel Code or shall comply with one ...
2018 Uniform Plumbing Code of Nevada > 5 Water Heaters > 505.0 Oil-Burning and Other Water Heaters > 505.4 Indirect-Fired Water Heaters
603.5.4 Water Supply and Distribution, Heat Exchangers
-transfer medium. Single-wall heat exchangers used in indirect-fired water heaters shall meet the requirements of Section 505.4.1. Double-wall heat ...
2018 Uniform Plumbing Code of Nevada > 6 Water Supply and Distribution > 603.0 Cross-Connection Control > 603.5 Specific Requirements > 603.5.4 Heat Exchangers
211.0 Definitions, — I —
Indirect-Fired Water Heater. A water heater consisting of a storage tank equipped with an internal or external heat exchanger used to transfer heat ...
P2801.6 Water Heaters, Required Pan
) in thickness. Plastic not less than 0.036 inch (0.9 mm) in thickness. Other approved materials. A plastic pan beneath a gas-fired water heater shall ...