// CODE SNIPPET
184.108.40.206.4 Incompatible Materials
JUMP TO FULL CODE CHAPTER
When the classification of materials in individual containers requires the area to be placed in more than one protection level, the separation of protection levels shall not be required, provided the area is constructed to meet the requirements of the most restrictive protection level and that the incompatible materials are separated as required by 220.127.116.11.2. [55:18.104.22.168]
Related Code Sections
22.214.171.124* Definitions, Incompatible Material
Materials that, when in contact with each other, have the potential to react in a manner that generates heat, fumes, gases or by-products ...
Fire Code 2018 of West Virginia > 3 Definitions > 3.3 General Definitions > 3.3.180 Material > 126.96.36.199* Incompatible Material
60.2.9 Hazardous Materials, Incompatible Material
See 188.8.131.52 ...
Fire Code 2018 of West Virginia > 60 Hazardous Materials > 60.2 Special Definitions > 60.2.9 Incompatible Material
184.108.40.206.4 Compressed Gases and Cryogenic Fluids, Incompatible Materials
and that the incompatible materials are separated as required by 220.127.116.11.2. [ 55: 18.104.22.168] ...
Fire Code 2018 of West Virginia > 63 Compressed Gases and Cryogenic Fluids > 63.2 Building-Related Controls > 63.2.3 Occupancy Protection Levels > 22.214.171.124 Quantity Thresholds for Compressed Gases and Cryogenic Fluids Requiring Special Provisions > 126.96.36.199.4 Incompatible Materials
188.8.131.52.2* Compressed Gases and Cryogenic Fluids, Incompatible Materials
separation shall not be required between cylinders deemed to be incompatible in gas production facilities where cylinders are connected to manifolds ...
Fire Code 2018 of West Virginia > 63 Compressed Gases and Cryogenic Fluids > 63.3 Compressed Gases > 63.3.1 General > 184.108.40.206 Separation From Hazardous Conditions > 220.127.116.11.2* Incompatible Materials
415.8.2 Special Detailed Requirements Based on Use and Occupancy, Separation of Incompatible Materials
separated from incompatible materials in accordance with the provisions of the NFPA Life Safety Code 2018 edition ...
Building Code 2015 of West Virginia > 4 Special Detailed Requirements Based on Use and Occupancy > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.8 Special Provisions for Group H-2 and H-3 Occupancies > 415.8.2 Separation of Incompatible Materials