3412.6.19 Incidental Accessory Occupancy
Evaluate the protection of incidental accessory occupancies in accordance with Section 508.2.5. Do not include those where this code requires suppression throughout the buildings, including covered mall buildings, high-rise buildings, public garages and unlimited area buildings. Assign the lowest score from Table 3412.6.19 for the building or floor area being evaluated and enter that value into Table 3412.7 under Safety Parameter 3412.6.19, Incidental Accessory Occupancy, for fire safety, means of egress and general safety. If there are no specific occupancy areas in the building or floor area being evaluated, the value shall be zero.
INCIDENTAL ACCESSORY OCCUPANCY VALUESa
|2 Hours and AFSS||-4||-3||-2||-2||-1||-2||0|
|2 Hours, or 1 Hour |
|1 Hour and AFSS||-3||-2||-1||-1||0||-1||0|
|1 Hour, or AFSS |
|AFSS with SP||-1||-1||-1||0||0||-1||0|
|1 Hour or AFSS||-1||0||0||0||0||0||0|
- AFSS = Automatic fire suppression system; SP = Smoke partitions (See Section 508.2.5).